Triangle tube challenger
Here is the start of my challenger job, first time installing one.
**** wrong place lol now how do I change it?
No idea but clean install
I guess if it never gets moved to wall of fame thats my sign to quit lol, thanks guy
Looks nice and clean.
Before you finish though, is it still possible to increase the distance of straight pipe going into your air seperator.
Those models need about 18" of straight pipe for laminar flow, so the air seperates from the water, and allows the scoop to "scoop" it up.
"Better tell the sandman to stay away, because we're gonna be workin on this one all night."
"Dude, you need more than 2 wires to a condenser to run a 2 stage heatpump."
"Just get it done son."
Lol I know but it's all cast iron rads so in reality it don't even need one, otherwise I would have been more concerned.
Originally Posted by hvacvegas
if thats WOS for you I wonder how good is your WOF install???
Have tools and gauges, will travel.
RIDGID|YELLOW JACKET|UEI|TESTO|STANLEY|CPS|VETO| KLEIN|MILWAUKEE|MASTERCRAFT|
Are you sure your "T" fittings are spaced close enough together? Is that a secondary LWCO at the top of the boiler loop? If so why? Looks clean, get one of the mods to move it to WOP
I r the king of the world!...or at least I get to stand on the roof and look down on the rest of yall
Post should be in WOP section.
The tees have to be a maximum of "12 apart, our inspector still requires a LWCO even though it has one internally. I think I will msg a mod, thought they would have done it by now lol.
Originally Posted by Wheelbaron
Jp please held I can't send a MSG for some reason but can you move this to walk of fame
Originally Posted by Joehvac25
Moved to wall of pride
Originally Posted by jpsmith1cm
Sent from my iPhone using Tapatalk