I have a question on a York YT Chiller. I getting High Oil Pressure faults. I looked though the information that I found on site and found that it will shut down the chiller at 60psi. I isolated and changed my oil filter it was pretty dirty and the oil was black. I Check both sensors/ Pressure Transducers they both read about the same with the chiller OFF. I put a gauge on the oil pressure filter after refilling with oil and I manually started the pump the pressure shot up to 110psig on my display screen on the chiller it maxes out at 60psi and then goes to XX.X for readings. Both my inlet and outlet valves are open I made sure of that. If you try to start the chiller it will fail in Prelube due to the high pressures. Any help would be Great.