Results 1 to 2 of 2
Thread: Andover Continuum to AX
10-11-2012, 09:32 AM #1Regular Guest
- Join Date
- Jan 2010
Andover Continuum to AX
I have a school that has Andover Native BACnet controllers in 17 of the new classrooms. We just took over the rest of the school, ver. AX 3.6.31 and I am trying to talk to these controllers to allow the owner to view the whole building from one graphic. I found all the devices after numerous discover, they can in a few at a time. When I went to discover the proxy points it took 20 min. but they did come in. Problem is they are all stale or in fault. This is the repeating error I am receiving.
at javax.baja.util.Worker$Processor.run(Worker.java) at java.lang.Thread.run(Unknown Source)
ERROR [14:02:06 10-Oct-12 CDT][bacnet.network] Bacnet Network Misconfiguration detected(1): Received message from network 2000 sent originally by us on network 2000!!!
ERROR [14:02:06 10-Oct-12 CDT][bacnet.network] Received Npdu indicates network misconfiguration!!!
Npdu: ver: 1 type: app pri: Normal DER: false
DNET: 65535 DLEN: 0 DADR: bcast hopCnt: 255
ERROR [14:02:09 10-Oct-12 CDT][bacnet.server] Bacnet Server Error!
at javax.baja.bacnet.point.BBacnetPointDeviceExt.find Points(BBacnetPointDeviceExt.java)
at com.tridium.bacnet.stack.server.CovHandler.process Cov(CovHandler.java)
at com.tridium.bacnet.stack.server.CovHandler.process ConfirmedCovNotificationRequest(CovHandler.java)
at com.tridium.bacnet.stack.server.CovHandler.receive Request(CovHandler.java)
at com.tridium.bacnet.stack.server.BBacnetServerLayer .processConfirmedRequest(BBacnetServerLayer.java)
at com.tridium.bacnet.stack.server.BBacnetServerLayer .process(BBacnetServerLayer.java)
at com.tridium.bacnet.stack.server.BBacnetServerLayer $ServerRequest.run(BBacnetServerLayer.java)
at java.lang.Thread.run(Unknown Source)
I have done a few integrations but never to Andover and I have never seen these errors.
10-11-2012, 10:29 AM #2Professional Member
- Join Date
- Dec 2011
- Charlotte, NC
I'm not 100% sure on this, but it may be a BACnet routing issue due to duplicate network numbers? It's been a while but I had the same error a while back with some other controllers if I'm remembering correctly.