Dapper, I have been searching for Trane info, LCI cards, etc., hooking up Voyager and Precedent to an automated system(using Tranes Lon), I have done a search on Trane on the site and notice you have numerous posts about doing what I'm looking for manuals on, if you could shoot me an email I would appreciate it.
Thanks for the info so far
I'm also looking for IOM
Trane Communications Bridge
I was hoping to go Trane-Modbus-to my controls without having to go the BCU route, but looks like in most instances Trane-Lon-Modbus-my controls is what I'm going to have to do
Trane Communications Bridge is a fieldserver box.
As far as I know you need the BCU to use it because BCU is feeding the IP side of the fieldserver box.
Trane LON --> Modbus --> ASI is the only way I think, if you want to stay on the communication level.
Hardwire is obviously always possible.
For LON to Modbus, if interested, look at:
at 256 variables in and 256 variables out, it is really a nice unit. Just so you are aware, these variables are passive (implicit), you will need a LON software to connect/bind trane's LON data to the gateway's variables.
[Edited by amigo on 10-03-2006 at 12:46 AM]
Dapper, Is there any chance that you could offer some help with a Trane LCI-I board. I am doing my 1st LON integration to one of those controllers. The xif file provided seemed to have more than a few duplicate snvts. I have not received any info from Trane yet, but I am expecting a response (soon I hope!). There is also some MP580s on this site also. They did not seem to have duplicate snvts - just a boatload of them!!
Oh well, any help you could provide would be appreciated.
Thanks in advance.
Put your e-mail in the profile.