I have a Jewitt Thermo Scientific under counter refrigerator. What is the minimum temperature differential setpoint I can use?
I have the temp set a 3C, with a 3C deadband. I timed it, and it was 6 minutes between cycles. I am concerned if I lower it to 2C I may short cycle my my compressor. Basically, Im trying to maintain a tight temperature swing.
Am I already as low as i can go, or should I go lower like 3/5?
It cools IcePacks, Basically its near 40F. They want a real constant temp, but I dont think my model offers that, (No capacity control, etc).