Before you finish though, is it still possible to increase the distance of straight pipe going into your air seperator.
Those models need about 18" of straight pipe for laminar flow, so the air seperates from the water, and allows the scoop to "scoop" it up.
Oooo, one of those little things. Nice to know.
True for Spiro too?
Which makes more sense to you? CONSERVATION - turning your thermostat back and being uncomfortable. Maybe saving 5-10% ENERGY EFFICIENCY - leaving your thermostat where everyone is comfortable. Saving 30-70%