Results 1 to 7 of 7
Thread: Rheem RPRL Heat Pump 501 tstat.
08-23-2012, 02:36 PM #1
Rheem RPRL Heat Pump 501 tstat.
I had a new split system installed last month (rheem rprl and rhpn 5 ton) with the comfort control 2 communicating tstat. My installer was not too familiar with the system. I notice the outdoor temp is reading 50 degrees more then the actual outdoor temp. I cannot find anyone who knows why this is. Would any of you guys have an idea why?