12K Mitsubish Replaced 4 Year Old LG
4 Year old LG Has bit the dust! Leaking Evap Coil and Sensor Issues. Replaced with new 20.5 SEER 12K Mitsubishi. This is a Daycare Classroom.
4 years? Yikes. I'm used to minis crashing around the 8 to 10 mark.
Sent from my iPad using Tapatalk HD
Nice pics. What are you covering the lineset with?
it was working.... played with it.... now its broke.... whats the going hourly rate for HVAC repair
Looks like the inside unit is crooked.
If it is, its a poor install.
Hide a line would look better on line set.
Nice. Is that sheet metal covering the lines? I've never seen that. You know, they make pads specifically for the mini split ODU's
America; first we fight for our freedom,
then we make laws to take it away.
-Alfred E Newman
Looks like the pic was just taken crooked. Looks good OP!
Originally Posted by HVAC/Stud
But do agree on the pad being a little on the large side. I prefer the smaller ones.
I actually like the idea of the hider being metal for commercial/industrial applications. Will stick to the plastic for resi
sent from my Samsung Galaxy Note
Member of the "Work Exchange Program"
"Will work for knowledge"
"Everyone is a genius. But if you judge a fish on its ability to climb a tree, it will live its whole life believing that it is stupid"
Thanks for the comments and input. The line set cover was existing. The pad was changed because the existing was just a foam core ultralite that had too many encounters with the weed eater! The reason for the full 36x36 does not allow grass to grow up behind the unit and get sucked into the coil when it is wacked down by the weed wacker. BTW the AHU is level. Just a crooked pic.