Find the Problel 8/2012
10 Ton Trane Pkg Gas Rooftop Install 208/230 V 3Phase
Is that green wire a ground ?
Sent from my SCH-I800 using Tapatalk 2
Looks like the line side wiring is undersized, in the pic it appears to be 10ga wire. Should have been at least 6ga wire going to that terminal block.
When you do a job, Always make it easier for the next guy, because you may be the next guy working on it.
It is at least a 6 may be a 4.
That's what they call a single phase conversion. Attach the green wire to the terminal block and it becomes 3 phase.
Officially, Down for the count
YOU HAVE TO GET OFF YOUR ASS TO GET ON YOUR FEET
I know enough to know, I don't know enough
Liberalism-Ideas so good they mandate them
There's a mess in the bottom left of the screen I cant make heads or tails of and it looks like one or more wires have the insulation tucked under the screw.
its 208 volts and the tap on the transformer is at 230
i was also seeing the insulation under the screw
Not sure if the middle leg got pushed in all the way. And why are there jelly fish swimming just below the terminal block?
Common sense isn't very common anymore.
10 ton 208/230 v 3 Phase Trane gas Pack. The Green wire is used as a HOT Leg of Power. And There is not a proper Ground to this unit. To top it off this is located on the "Former City Hall" Where the Inspectors office was at the time of install 10 years ago.
Originally Posted by AC Shop
Inspectors are NOT about safety, they are about an easy income... Actually, to a degree they seem to have an entitlement mentality (like everyone else on the govt dole... payroll or non-working).
Quality work at a fair price with excellent customer service!
Romans Ch's 5-6-7-8
2 Chronicles 7:14
Got a little warm at one point, did it?
Please excuse me if my post looks like it was typed by a teenager. It was sent from my phone.
I do three kinds of work.
1 - Good - 2 - Fast - 3 - Cheap
Electricity does not care what color the wire is.