After replacing two redundant chilled water pumps we have had constant air on one side of our chiller plant. The pumps and piping were refilled up to the check valves after recommisioning. Our tech's bleed the air off and 48 hrs later it is back. luckily it hasn't moved to the rest of the system. Is there anyway to find the air leak on the suction side of the pumps? Other ideas?