5 ton scroll compressor in a split system.
It is a 3 phase compressor, pulls 30 amps from the get go and will go all the way to 40 amps (and shut off)
The winding(s) resistance is about .5 ohms on all of them. It also doesnt sound great when it is running. I recovered 20 pounds of refrigerant from this system, recharged with around 7.5 pounds... After cleaning the ridiculously dirty evaporator.
Just looking for affirmation, thank you for your input.