Results 14 to 15 of 15
08-14-2012, 05:56 PM #14"Better tell the sandman to stay away, because we're gonna be workin on this one all night."
"Dude, you need more than 2 wires to a condenser to run a 2 stage heatpump."
"Just get it done son."
09-13-2012, 02:30 PM #15Regular Guest
- Join Date
- Aug 2012
- Tampa Bay
I just wanted to give you all an update...I had a good company come out and increase the size of two of the return runs and the riser (now rectangular ductboard), and replaced the mixing box...they also needed to add 4.5 LBs of freon (which surprised me) and re-adjusted the blower profile to 20° F split across the coil...wow...what a difference! The house is now cooling at whatever temp I set it to (75° F) and is operating at normal pressures etc.
Thanks again to everyone for your advice and suggestions.