I had a brand new trane installed in april. I have been wondering why my humidity spikes everytime the unit turns on. Well I noticed a decent amount of water in the drain pan. I looked inside AH, and noticed insulation very wet, and looking inside i noticed the coil is reversed! The bottom of the "a" is facing the blower, return air is passing through the top of the"a". I see water dripping down...and I assume is blowing through the blower and into the ducts when its running, and i guess is why the pan is filled.. The coil sounds like its reversed...correct??? I will be calling installer tomorrow. Should i request a brand new AH since its been getting wet since april? Thoughts and suggestions please. Thanks.