I just installed a frigidaire 2 ton system, 14 seer heat pump with a b6vm fan coil. Upon power up it gets a signal from the stat and then the fan coil board and blower motor board start blinking red, while the green light stays on solid. In the instructions it is indicating a motor fault with no steps to properly correct the issue. There is a brown and gray harness coming off the motor that is not plugged in, but I see no female end. The blower does work for about 30 sec upon power up if there is a call then the led's blink red. Any ideas on how remedy the problem? Dip switches are set properly. Thanks in advance.