Results 1 to 13 of 20
Thread: where to draw the line
07-19-2012, 10:08 PM #1
where to draw the line
At what point do you call out your coworkers and tell them to straighten up. I went to a call today for a keg cooler today. I arrive on site to find a blown breaker for condenser. While I'm looking around I find evaporator thermosat set to 10 degrees. Wires hanging loose with wire nuts all over the place. Solenoid coil overheating because screw is loose and wire connections look atrocious. I was embarased to say it was a coworker that did this. Then I find the wrong fan blade is installed and is going backwards. But i reset the breaker for condenser and it immediately trips. I go to roof to find compressor shorted to ground. So i qoutr the condenser pick it up and install. Clean up wiring inside the box while i evacuate and install proper fan blade and redo drainline that was taped to pan with electrical tape. I go back to roof charge system and find I now have a bad txv. Back downstairs and look at my danfoss valve and it is ziptied to suction line not insulated and at 12 oclock. So I move to approx 7 and insulate and open all the way up and can still only get 40 degrees superheat but much better than pumping into a vacumn as it had been. So i ordered the new valve.oem along with new evaporation motor because that wrong fan blade had worn out the bearings. I'm sorry for my terribly long run on sentence and if i was unclear let me know. But what a terrible day fixing somebody else's crap. Should I just stay quiet or should i tell the boss that one of his favorite super techs is a hack. The hack part is just my opinion.
07-19-2012, 10:13 PM #2
i wouldnt tell the boss .. id tell the hack what you found & what you did to make it right .... tell him that type of sh!t doesnt fly & will only make the whole outfit look bad if anyone ever catches on ...
07-19-2012, 10:22 PM #3
07-19-2012, 10:39 PM #4Professional Member
- Join Date
- Jun 2009
- Garland, TX
Start taking pictures and sending it in if you can. If the owner of your company has any pride he will correct the situation.
Also what I do, is I just document exactly what I found. Then when my manager is reviewing the invoice to see why a lot of my time is not billable, he can see exactly what I had to clean up.
Yes it is very frustrating when this kind of thing happens, but I think every company has techs like that. And sometimes good techs just have bad days too, although what you are describing sounds pretty extreme. Some techs just don't care, and some are trying the best they can but they aren't that good.
07-19-2012, 10:40 PM #5
he did all of that??
07-19-2012, 10:48 PM #6
07-19-2012, 10:55 PM #7Originally Posted by hvac wiz 79
Start by sending them to the tech.
Then, if that gets no results, send 'em to the
07-19-2012, 10:56 PM #8
I wouldn't go to management, because then you're an underhanded back-stabbing coward. I also wouldn't throw him under the bus on my service ticket, either. Remember, the customer sees those, too. They're not stupid, and they can read between the lines.
What I would do is have a conversation with him first about what you found and explain that you don't like cleaning up others' mess. If it continues, refuse to follow up on his calls. If the boss asks why, then tell him/her.
At the end of the day, you can rest easy because you know you gave the guy a chance to get right. Some people fire themselves.Truth is still truth, even if no one believes it. A lie is still a lie, even if everyone believes it.
"It's called the american dream because you have to be asleep to believe it" -George Carlin
"A nation of sheep begets a government of wolves" -Edward R. Murrow
"I have problems just like you. One time, my dancing horse almost fell into my car elevator" -Mitt Romney
Buy american made goods & support locally owned businesses!
07-19-2012, 11:55 PM #9Professional Member
- Join Date
- Jun 2009
- Garland, TX
1st, I am very honest and open with my service manager about everything. The majority of the time, it's my own mistakes that I bring up. That's part of why I think he trusts me so much. In my opinion, he needs to know strengths and weaknesses of other technicians.
2nd, I always talk to the technician first before I speak to service manager about the situation. Nine times out of ten, there's a good reason why the other technician ignored all the other issues; often the customer didn't want them to spend time cleaning up wiring, drain lines, etc. Or it could be because the technician wrote an estimate to repair all of the minor issues, but I didn't know it and the customer never approved the estimate, etc. Or like I said originally, even a good tech can have a bad day and make a mistake.
3rd, we have electronic invoices and our customers don't see a "callback" invoice - the callback invoice goes to the original technician who was out there, or just to the service manager. So this is one way I can communicate clearly what I found.
Thanks you made a good point.
07-20-2012, 12:12 AM #10
I phone up the guy on EVERY callback. Not an ass chewing, just a 'this is what I found' deal. If he has pride, things will change. If not, talk to the boss. I also tell every guy that I want a call if they follow me.
07-20-2012, 12:24 AM #11
Might be laziness, might be cheap customers, might be a guy who was never taught properly. Continue to do quality work yourself. Build a good rapport with the customers. Drop hints to them to ask for you when they place a service call, or to say "Just don't send(fill in tech's name here)" The shop will get the hint. This way the customer is throwing crappy tech under the bus, not you.Local 597 Service Fitter
Metal Trade Journeyman
PAY ME NOW OR PAY ME LATER
It was working when I left...
07-20-2012, 07:41 AM #12
I'm just tired of people going out and hacking stuff up. And the bossman looks at me and wonders why it takes me so long. O could give a hundred examples. The boss thinks this tech is the best. And he is a smart guy but I don't know why he does some stuff.
07-20-2012, 07:49 AM #13
i had to go behind the owners son one time on a call back . Reach in beer cooler wouldnt get below 48 . Found the high side way high. First thing i notice is the fan shroud missing. I ask the cook in the kitchen , did anyone remove this shroud ? He says yes the other guy who worked on that said by him removing the shroud it will allow more air to cross over the compressor to cool it.
I gather up some tin foil pans and make my own shroud.
Never heard a call back since.
Never mentioned to the son what i did ....