The TXV was changed from the factory Danfoss to a Sporland, The equalize line was check for flow. All checked good. Air flow was double checked by checking pressure drop a crossed the coil. .58wc the valve checked good the heat added and then dip into and ice bath, responsive to both
Fair enough...for a while there, I thought you had burned down the house to get rid of the cockroaches.