My heat pump compressor will start and run for three seconds and suction line will get cold than it shuts off for twenty seconds than restarts for three seconds and continue to do this until it shuts of on internal overload.
The unit is a Goodman with indoor unit being a janitrol.
outdoor unit model #cph36-1fb.
evap coil is not frozen, appears normal
air filter is clean
indoor blower working
tstat operates outside contactor to start compressor and fan, however compressor cycles as above while condensor fan works normally. Contactor does not cycle, it stays energized. Last maintenance done was to add freon last year.
Unit was maintaining indoor temp of seventy four degrees until I decided to go outside and inspect. All I did was remove the access cover to look at compressor, when it started to cycle and now it will not maintain indoor temp at all. I thought I might have disturbed something when I removed cover. There is 225 volts at contactor.