A 12 degree temp drop is low. The 82 suction psi sounds high for 78 return temp. If the suction line is 48 degrees it is slugging the compressor. What was the outdoor temp when you checked the pressures. Something is not right, is the equipment a matched system. It probably needs to be looked at.