Started 9am left with system running at 12:30pm.
2 Ton Lennox 13 SEER 410 condenser with a c33-24a-2f evap, no txv changeout from r-22.
When done, I had 21f temp drop. 37f at first supply.
Ambient at half past noon was 101f.
I left the tstat at 72f and asked her to call me when if satisfied. She called at 3:45 saying it had reached 72f and temp right now in Atlanta area is 102. Im very happy with this install since I didnt encounter any hang ups.
Flushed line set with rx-11, nitrogen press test and sweep. Vacuum 30 min, (without micron gauge... I know, I have to get one)