I have a Trane Air Handler - 4TEE3C04A1000 paired w/ an XL20i installed in a garage. The top section of the air handler / blower section has an accumulation of excessive amounts of mositure - saturating the insulation lining the front cover panel and the electrical and electronics are also covered with condensation.
At times the water runs out of the front panel.
The exterior does not have any condensation on it - this only exist on the interior.
The CFM's are set for 400 per ton. Condensation line is draining.
This does not seem normal to have the interior so wet and with wet electrical components.
Does any one have a suggestion or has seen or experienced this before.
Thanks for any input...