Results 1 to 8 of 8
Thread: Don't forget the pookie...
06-27-2012, 06:19 PM #1
Don't forget the pookie...
Call on a small W/I freezer- An old Hussman condensing unit on the roof. The unit breaker was tripped- reset and BAMMM! Flash and trip.
Took a while to find it, but a feed to the LL solenoid valve from the control panel was connected by a close nipple with plastic bushings on both ends.
There was slack in the wire (#16 THHN) to the coil,but it still wore through the bushing till the hot leg hit the nipple. BOOM!
Took about 20 years, but...
A little pookie stuffed in the hole... might have save the problem.Experience is what you have an hour after you need it.