I'm working on a walk in with two evap coils on one condensing unit. R22/ suction is 45 /head pressure is 250. Ambient temp is 95. One coil has a 9 degree superheat but the other has about a 20 degree superheat. Seems like my coil is starving for freon. Doese this sound like an expansion valve issue? What else may cause this?