High Efficiency Gas Boiler with Iron Radiators and Pipes?
I live in an older home with hot water oil heat and big old iron radiators. I am in the process of getting estimates on converting to natural gas. My current boiler is pretty new (8 years).
Two people who have come by have told me that I should just convert the burner given the age of the boiler. Further, one person told me that a high efficiency boiler has lots of condensation that would be a major service nightmare with iron radiators and pipes.
The man identifying where the gas meter would go also told me that I should do a conversion, and that folks would try to sell me a new boiler when it wasn't necessary.
So, a third guy was just out this morning who told me that I would be very disappointed in the savings if I didn't go with a new high-efficiency boiler. He told me that the condensation would not be an issue. He also said that converting it would be very inefficient -- lots less than it is currently with oil -- like it would end up being around 70%.
If anyone can give me any insight on this, I would be very grateful. Thanks so much!
I usually recommend replacement of the boiler with a high efficiency system.
Some of the things you are being told are true.
When you convert a oil burner to a gas burner you lose efficiency.
This is true and it typically is around 70%
What is also true is that you are going to still save some money with converting from oil to gas. I am not sure what you are spending on oil or gas. But for example
oil at $3.75 Per gallon burning at 80% efficiency would cost $33.80 to get 1 million Btu's of heat.
gas at $1.15 per Therm at 70% efficiency would cost $16.43 to get 1 million Btu's
and gas at $1.15 per Therm at 95% efficiency would cost $12.11 per 1 million Btu's.
So you can see that natural gas at today's prices cost much less then oil despite the loss in efficiency.
High efficiency boilers do create condensation but it is all internal in the combustion system and has no effect on the piping or radiation system.
One place I am not seeing mentioned is what is being done with the chimney if you do an oil to gas conversion?
If you have an old brick chimney you really should have a liner installed to make sure the system vents correctly and does not damage the chimney.
One other concern with most oil to gas conversions is that it is not what the manufacturer intended for that system. You should make sure that someone checks with the manufacturer and make sure that its ok to convert it.
I have always been uncomfortable with the conversion idea, but I am a salesman not a technician
Good luck with your decision, anyway you go you will save a ton of money going to gas.
you contract must know how to properly pipe the new boiler. It IS possible for condensation to be created in the boiler if precautions and piping techniques are not followed. And as was mentioned, you will probably need to line the existing chimney (unless of course they use PVC for the intake and combustion vent).
GO NAVY, BEAT ARMY!
A DECADE OF DOMINANCE! +3
Hello Mary, so many choices...
There is nothing as good as those high mass rads. Keep them as long as you can. Also the opportunity for reset ( lower ) water temps that match the load is an area that needs a contractor who understands BOILER PROTECTION ( how to avoid condensing with a boiler that is not supposed to condense
Originally Posted by MaryO
You have got to learn from other people's mistakes! Because God knows you don't live long enough to make them all yourself !!!!!!!!
This is the Ask Our Pro's forum. In order to post a response here, you must have verified qualifications and have been approved by the AOP Committee. You may ask a question by starting a new thread.
You can find the rules for posting and qualifications here.
Additional infractions may result in loss of posting privileges.
Your post has been deleted.