mitsubishi lm adaptor integration
Has anyone integrated the mitsubishi with a jace (trend TONN6)? Im having some problems with this system.
I have not done a Mitsubishi integration but have done a few others.
I have worked with Tonn,Hawk & Jace. I may be able to help.
What exactly is the problem?
We have done daikin and Sanyo, but this our first Mitsubishi. I just can't pull in any points and the lm adapters keep freaking out, and Mitsubishi tech is about terrible in helping out.
Have a look at the Lonworks help file in workbench.
It has some usefull pointers to the 'Lon Utilities Manager' this may help you identify a timing issue perhaps.
Also have a look through the 'About Lon Network Architecture' in the same help file. There are some good pointers in this which may help you.
I take it that you can see the devices on the lon network when you do a learn. but then you cannot discover the Nv's & Nc's of each device.
Do you have a lon adaptor in your laptop? if so then try and run up a station on that and connect locally, try the learn process again. If it works then it could point to a wiring issue.
Just a few thoughts.
yes, you are 100% correct. I did that over the weekend and got all my points pulled in and everything working correctly. Thanks!!
You may want to look at this site as well to make sure. I just did one and I was able to see everything but to prevent local setpoint control and scheduling the documentation is essential.
Originally Posted by clynn
It is the Mitsubishi Site for their LON interface.
You can easily judge the character of a man
by how he treats those who can do nothing for him
-James D. Miles