Got a call last nite the this stores three RTUs were not cooling. Go up on the roof this am and find them frozen up like blocks of ice. Come to find out someone stole the main electrical cable over the weekend. Electricians never checked their phasing so the fans were running backwards.
Sent from my iPhone 4s