This is always how it starts....so I have a friend of a friend who wants a 4 ton HP install. So my friend installed this unit for him. For some reason he thought that 13 seer hp's use r410a. So he fired up the system and added about 1/2 a pound of r410a before he notice that it's r22. Question is... what are the potental problem?????