possible coil restriction or blower failure. another thing i like to do is turn off the blower motor and see if the entire coil freezes. if you had a restriction in a cap tube, that part would not freeze because there is no refrigerant in the circuit. i would check airflow. maybe there is a eddy effect at the bottom of the coil which is restricting airflow and only the top half of the coil is getting flow.