there on a 10 ton split system for A/C. Originally it was a water cooled air handler. Someone added a air condenser on the roof. Two 5 ton Copeland CRN-5's on separate circuits. Hot gas goes into separators then up to roof. The one dead compressors separator looks like a major leakier. I would like to cut it out and bypass it. Yes, No, or Maybe ?