BIGERNXXL, this is the Ask Our Pro's forum, and only Pro members that have been vetted by the AOPC may post advise here. Please apply to the AOPC today, thank you.
You can find the rules for posting and qualifications here.
Further infractions may result in loss of posting privileges.
Very simple Store is under negative pressure... to confirm with all doors closed open one door a couple of inches while you are inside the building at the door that is being opened and if you feel the outside air come rushing in at you from the door that you opened ... and all belts at tight on AC units , and if they are...
Store needs to be balanced...
Hope this helps
Isn't sanity just a one-trick pony anyway? I mean, all you get is that one trick, rational thinking, but when you're good and crazy, well, the sky's the limit!
Better still light up a cigarette and walk around blowing smoke and see where most of the air infiltrates and seal that. Then crack open a window and measure the air volume going in (velocity x area) and run an OA duct to your return sized based on this info plus the calculated the leakage around the doors and some extra to get your positive pressure and do this with your kitchen exhaust running. This should correct your negative pressure. Thank you very much
Originally Posted by skpkey9
"I could have ended the war in a month. I could have made North Vietnam look like a mud puddle."
"I have little interest in streamlining government or in making it more efficient, for I mean to reduce its size. I do not undertake to promote welfare, for I propose to extend freedom. My aim is not to pass laws, but to repeal them."
I would also bet the building is negatively pressurized.