Results 1 to 13 of 19
05-01-2012, 09:53 PM #1
Coil Replacement on Carrier 10 Ton
Thats not the worst of it. We quoted the job to replace the coil that was stolen and the building owner gave the job to a family member.
Guess he didn't have an account at Carrier.
05-01-2012, 09:58 PM #2
Is that 2 5 Ton splits hooked up to that Evap coil in the RTU?
I wonder how much money he saved?
Some people I don't know EH?
05-01-2012, 10:16 PM #3
I am pissing myself!!!
LOL! It's a friggin 2-stage!!!
HA HA HA HA HAEvery customer you take for granted today will be someone else's tomorrow.
05-01-2012, 10:30 PM #4
05-01-2012, 10:32 PM #5
Holy cats, does that actually work?
Sent from my iPad using Tapatalk HDTo the man who always did it right. I love you dad and I will miss you to much for words.
Stay Thirsty My Friends
Support the Skilled Trades Don't DIY
05-01-2012, 10:37 PM #6
Thinking outside the boxLocal 597 Service Fitter
Metal Trade Journeyman
PAY ME NOW OR PAY ME LATER
It was working when I left...
05-01-2012, 11:18 PM #7
05-01-2012, 11:23 PM #8Professional Member*
- Join Date
- Nov 2004
- Austin, TX
A conversion of a package unit into a split system. Hideously clever. It's not all bad, the service ports are easier to access and the controls are simplified. You don't need to replace the panel to check pressures. Won't be burning your forearms on the hot discharge lines when you are putting the gauges on.“I am for doing good to the poor, but...I think the best way of doing good to the poor, is not making them easy in poverty, but leading or driving them out of it. I observed...that the more public provisions were made for the poor, the less they provided for themselves, and of course became poorer. And, on the contrary, the less was done for them, the more they did for themselves, and became richer.”
― Benjamin Franklin
05-01-2012, 11:31 PM #9
It does work to some degree. A coil would have been a lot cheaper but thats assuming the AC contractor didnt steal the condensing units. The high voltage is wired to the line side of the compressor contacts. Low voltage is wired in at the low voltage terminals Y1 and Y2. They're jumped so the entire cluster......... starts up all at once.
05-01-2012, 11:41 PM #10
thats just wrong......it did make me laugh though
05-01-2012, 11:41 PM #11
05-02-2012, 12:05 AM #12
I agree butchers......
05-02-2012, 12:58 AM #13
If it had been done more neatly, I wouldn't have a problem with it.
It isn't something I'd do though.If more government is the answer, then it's a really stupid question.