I was sent to give a free second opinion today and this is what I found:
Expulsion was blanketed with about 1/2 inch of debris...not exagerating. After I cleaned it this is what I had.
Comp amps 14.3
LRA listed at 15
50 low / 140 high
Con coil could use some attention as well as blower wheel but not clogged.
Added some r22 and brought my low side to 60 psig with a super of 25. High side and sub didn't move.
I do so few pkg units but I'm thinking the clogged evap coil worked the compressor too hard and now it just won't pump any more...condemn the compressor or the whole unit due to condition of coils?
Thoughts or suggestions?
Sent from my ADR6350 using Tapatalk 2