Hi all, Have a 40 ton AquaSnap that keeps tripping out on A207. Both EWT and LWT thermistors are both reading correctly. Also have 15psi across the exchanger. Both of those are the listed diagnostics in the troubleshooting manual. What is happening is 2 stages are starting and continuing to run at 50% capacity without staging down. They cycled down in the past. Also noticed that even though the A1 compressor relay is "OFF", I'm getting an "ON" for the A1 compressor feedback. My control setpoint is 50°F. Unit keeps running until LWT is 33°F and then tripps. Any ideas? It's a glycol unit, digital scroll and the correct fluid is set in Option 2 of configuration. Control mode is set correctly also (0). My clsp1 is set for 50°F and my brine freeze set point is set for 32°F. It is running in Local Mode and not on CCN. Thank You!