I usually hold hospitals, labs, colleges, etc. to the thought that these buildings house people of great logic. Thus i figured they would hire people who were the best in their field to maintain these facilities.
I thought wrong.
These two are 3 ton York air handlers that they said they always had a freezing/melting/leaking problem with. No one could figure out why. Turns out because of the urine smell in this area, they are required to have exhaust fans. Only bad part is that the dummkaufs that put the fans in, tapped into the returns of these units. So as long as the mushrooms are running, there is no return air to the air handlers. 3 contractors couldnt figure it out, but one of them knew how to make sylish access panels.