Have a Scotsman CM 1200/1400 units takes 6 min before water temp cold enough to begin ice building then sump runs out before cubes are ready.
Question 1- is the refrigerant change from r502 to HP80 affect this time
Question 2- wheres is water going (drain is overflow tube not a valve) if I overfill sump it will run for a few batches before running too low (cleaned inlet valve) Any help or ideas would be appreciated. Thanks.
Someone else has replaced timer motor, receiver, head press control and expansion valve and removed inlet strainer. I came into this after the fact.