I mainly work on commercial refrigeration(I.e. Supermarkets) but I was called out on fire alarm caused by an HVAC smoke detector. I found only one of five AHs with a tripped detector on the boiler sys. Removed cover and checked filters, screen and tubes on detector, all clean. The air filters were fairly new and the blower belt is external. Any ideas on what may have caused the detector to trip?