Mini split wall unit need to reverse piping
Installing a gree heat pump and need to bend the evap piping to go the other direction. I know there's away to bent it and not kink it.
a 3/8" pipe bent 180 * needs what 4"
a 1/2" needs 6+"
No way of putting a u-bend behind the unit without opening the wall
Post Likes - 1 Likes, 0 Dislikes
remove flares braze in fittings , use nitro to prevent oxidization
IF,your talking 90 of the HEAD piping,Just bend IT.
With 1 hand AT the 90 from the ecoil and the other hand at the Flair End and,
Just sweep IT 'around.
No 'Big Deal bud,just Do It.
No matter how long you have been doing this,
Go back and reread the Basic's.You WILL Learn something.
Why is it called,an Act of GOD when IT has Nothing to do with Him?
Will of the Devil would be more appropriate IMO.Just Saying.
PSALMS, 18 & 25.
I've done this before. If its less that 1 ton and uses the smaller 3/8 and 1/4 lines than you can carefully bend it without a problem. You might have more problems with the drain though. Just make sure to pure some water into the catch pan and make sure it all drains out.