Type: Posts; User: chrisevansac
It's a gmc
He needs to get his post count up.
All three legs getting 208v. How much drop would be questionable 5%?
I reset the unit and the compressor pulls locked rotor amps then the controller gives 3 flashes and continues to try and restart. Seems like the compressor is locked up. Any insight?
4 flashes on the Emerson digital scroll locked rotor code. I've never worked on one so is there a way to unlock it or is it still like a regular compressor and needs replacing?
Why not tell them?
Anyone else's break that quick? Supposed to be professional grade, and they break when I squeezed them. :gah: other than that I'm pleased with them.
Carrier performance series or getter. Quietest units I've installed
I've got the hilmor. Less parts and pieces
Also insulate the condensate line
R-8 is plenty. I would look at duct construction and see if its properly sealed with mastic. If not it doesn't matter if you have r-18 it will condensate where the air is coming out of the seams...
In my experience the only coils that didn't work were the capilary tube type.
The ta071 needs 18gpm I believe
Looking into geo. if I were to install a 6 ton Bosch ta series and flow center. Would that be all the pump I would need? Also would one well open loop pump and dump set up work?
Keeps the liquid from flashing off too early by not letting it absorb any heat
None. But it does pass through the defrost board.
I'm going Saturday to sit on a bucket
I was thinking overcharge. The high pressure and low pressure cut outs were my next guess but I didn't think they would cut back in that quick
Got a brand new Payne heat pump that will come on for 2 seconds then off about the same time then on for 2 seconds then off several times before staying on. Of course I'm not there when it happens....
Had me going
Why is that
Measuring at evap. But the unit is still running.