Type: Posts; User: ClassicDave
Search took 0.01 seconds.
sounds sort of like my problem,
system 5 yrs 3 months old, compressor out of waranty:
No Cool Call:
had a bad capacitor, replaced and left. Two hours later called back not working. Went back...
I pulled the refrigerant back using the compressor, locked it down and pulled the disconnect to the condenser and shut off the breaker to the air handler.
I took the old txv out, put the new...
went got a txv replacement.
Got to customer's home, pressures were 25 suction 205 discharge pressures.
recovered refrigerant back to compressor, that went well
removed txv, cleared...
Weather King 3 ton heat pump, R-22 Bristol compressor
system not cooling, 5 years of no issues.
Found bad capacitor replaced capacitor, rheems plastic capacitor bulged on top, replaced cap...
I do a lot of zoning and I fix a lot of other attempts at zoning.
My favorite zone control is the Bryant Evolution or Carrier Infinity Zone Controls with their communicating system....
Actually there is only one difference and it is in marketing
The Carrier is a National Consumer Market, while Bryant is a Contractor Dealer Market
There is only one difference between the two on...
A pretty good summary. I can't disagree too much, but as you might have guessed I do have some comments.
1. The HC16 and the Carrier Infinity or the Bryant...
The Perfect Air Purifier produces only around
5ppb (parts per billion) ozone. The EPA recommends no
more than 50ppb for a healthy living space. In most cases, the
ozone output will be below the...
Definitely look into a system that at least qualifies for a tax credit.
Most important, the systems that qualify get you out of a RNC (residential new construction) models. Many A/C guys love...
If you have purifier, remove all other filters. The purifier filter is the only filter that should be used. Any other filters being used at the same time more than likely will cause high static...
There is always the other option.
Go with hybrid heat and qualify the tax credit under heat pump.
Heck as long as you get an Infinity Furnace 58CVA and the Infinity controller you can then choose...
on #3 it says
A Manufacturer’s Certification is a signed statement from the manufacturer certifying that the product or component qualifies for the tax credit.
I have not seen...
The thing is and someone may answer the question, what is exactly a Advanced Main Air Circulating Fan? To me it is not a variable Speed Fan Motor in a Furnace.
I could be wrong though.
Well since this post is old, and the original poster is probably enjoying his Bryant.
So I would have to agree that Bryant was a very good choice! :D
95% gas furnace and above,
Sorry 80% is a no go.
next the truth to the Weatherization Deal,
you want to look, how much you made this year.
and what your taxes paid or received was.
Tell your hack, you want a Bryant Evolution Hybrid Heat System with the Evolution Controller!
They are sweet! oh he probably doesn't know how to hook it up because it is over 13 SEER.
What is the temperature when Celsius and Fahrenheit are the same?
Times up, you lose!:p
Learned that in the 5th grade from a bonus question we all got wrong! Amazing I still...
5 Ton Ultra High systems drops tremendously in effeciency compared to a 4 ton.
If you can go with a 4 ton that is the way to go. Plus most ultra high efficiency systems need 1 1/8 suction copper...
If you can fit it go with the FE4ANF006 gets you a better SEER and HSPF rating.
If the dealer is going to go up only 500 on the 19 go with that. 19 has a varable speed condensing fan motor and 2...
I sent the guy an email.
Felt sorry for him after I found the closest Bryant Factory Authorized Dealer was 90 miles away, no Factory Carrier Dealers to be found. Only 2 Carrier Dealers with in 20...
SEER rating should be upgraded.
I like to see a $2000 consumer voucher to be applied to a 2 speed systems that meet 16 SEER or higher.
Talking about saving energy in the USA that would do it....
My system is a 12 SEER Rheem Heatpump
RBHA-21J11NFGAI Air Handler
TXV indoor Evap and TXV to outside Condenser.
Roughly 8yrs old.
I'm going to post...
I have a similar situation
many have stated the txv in the condenser to be the issue.
I have ordered a TXV for the condenser and will be putting it in on Friday.
Doesn't matter if it works or...
Take this post above seriously.
I am changing out a TXV on my mom's rheem, just ordered it.
I have extensive experience in zoning. I also fix a lot of messed up zone installations.
Believe it or not, It really depends on your design of your home. Attic Space, where the Air Handler is...