Long story in a short version....if it is tripping on thermal overload...then not enough COLD freon is getting back to the compressor...either TXV...or coil...make more measurements to find out which
Type: Posts; User: rmeader45
Search: Search took 0.01 seconds.
Results 1 to 9 of 9
Used Equipment - Buy, Sell, Save!