Type: Posts; User: sraburne
Search: Search took 0.01 seconds.
I have been servicing for about 7 years, a 70-ton Mammoth cold deck 1984 unit that my customer would replace. The 2nd stage 30-ton Part windings start compressor, during heavy loads is tripping off,...
Worked on a snow melt boiler system that has not been serviced in approx. 5 years since it’s install. The only reason we were called out was the boiler was not running, found to have a bad inducer...
I replace it with the 440 volt rated capacitors. I guess, will see how it does. Thanks again, Steve
I Had a upflow furnace blower not running call about 30 days ago 5/23/07. Found the blower motor hot and running slow' with high amps. Tested the run capacitor,tested bad,rated at 10mfd getting...
Results 1 to 4 of 4