Type: Posts; User: roadking44
Jets going to spank that a**.
I can view when im not logged in but when I log in it gives me this page.
roadking44, you do not have permission to access this page. This could be due to one of several reasons:
I think so. Is this a private forum now? Still not letting me in.
Is there still a trickes of the trade forums?
Used to smoked 2-1/2 packs a day for 30yrs. but now i've been quiet for 1 1/2 yrs. Chewing the hell out of gum right know.
Shout chiller off and see if level comes up to +1.1. You can get a sight glass and hoses to check level in barrel. If you shout it down and senor does not move then either float stuck or sensor bad...
I've never heard of Rittling. I would be scared I wouldn't be able to get parts years down the line. I Just started up about 150 trane fcu's and they work great. Never seen a McQuay fcu in a while...
I used to use a usb to 9 pin adaptor on mine. Still have to have teck view to see anything.
You probably get more response if you post this in the control area.
I just use a two old hoses and a sight glass in between for checking level. I use clear hoses for charging centervacs.
I hadn't had any leak either.
Could have a bad regulator.
We hadn't had that problem here (ms.) What is in the kit? I work for Trane and seen a kit.
You dont want to order nothing from the factory right now. They are about 1000 orders behind because of the...
We work on alot of Munter units and have not heard that. Still selling them down here.
They bought Trane several months ago.
Put the vaccum gauge on your pump and make sure its pulling down to a couple hundred microns. Make sure evap. and cond. water valve are closed tight. Make sure there's no flow through chiller. You...
The guy who got fired with us was spending more time at his tobacco store then at work. We have 46 trucks on the road so it stopped people using them after hours. Was long as your honest then you...
Yea, We've had if for about 2yrs now. It's already got one guy fired. They can tell where you are and how fast your going and if your truck is idealing for more then 30min. We've got use to them.
I've replaced one on a rthd before. Have to reclaim freon and unscrew float from the bottom and replace. Go in tech veiw and rebind llid. Not bad but just takes a while to reclaim freon.
Sounds like a low end surge because of no load. Trane bad abou that. Put a load on it and it will go away.
Bet its low on refr. oil logged evap. Leak check solenoid valve around gas pump that going from pump to condenser ( drain solenoid valve). I bet its leaking when its entergized. I leak checked one...
Slide valve is not bad. Just order a slide valve kit. It will have a gasket and round disk ( slide valve). Valve out compressor and take discharge plate off and you will see slide valve. Swap out...
Stuck slide valve will cause that. We change lip seal all the time in field. Most likely it's just slide valve.
Looks good! Not sure about how long arm will last but screen is real sharp. Does anybody know when they will be installed on new chillers and if they will come installed on door instead of arm?
Slide valve stuck loaded. That's why its starting at 85%. Replace slide valve and we normally go on and do lip seal to if not already done. Cuts down on another call later.