Type: Posts; User: hs2kang
Search took 0.01 seconds.
Thank you for your comment.
I have exactly same problem at a KFC. The problem can not be reset by just turning controller off/on, but can be reset after disconnect/reconnect the harness between...
It is R22, txv which have low suction pressure problem(30psi).
Sight glass was full of R22. Clean evap'. Head pressure was 190psi.
Somtimes show frost on suction line near comrpessor like...
No. Also I didn 't change drier bedause I didn't open the system.
Anyway, manufacturer decided to replace whole unit becaise they don't waste time.
Please look at my 1st post.
I trid it alreay. I trid to recover refrigerant slowly watching pressure and temp.
Of coures, pressure down followed by high SH and box temp' up.
So I recovered all and...
I am new in refrigeration field started in May from residential HVAC, I already asked company's senior tech.
But answer wan not clear.
So, what is right answer by your nephew?
It is made by ATP, small local company.
At first, I thought the assembler installed a shorter cap tube.
But manufacturer said it was tested in the factory.
(This is manufacturer approved warranty...
Hey everyone i have a Reach In Cooler giving me problems, its brand new one installed in April, never worked properly.
The problem is that unit never run below 50*F. Its cap tube systme, R-134A, 2...