Type: Posts; User: traneman1
UA Local 602 Wash. D.C.
hey mallron you are in 602 right? I would also reccomend the 0 to 3 inch mag.
3.1 I will try to get you some info.
Here in Wash D C Local 602 Steamfitters is 56.00 a month
Hey Johnny, did you check the fan request relay? I would also check the 1U1 . The only things that will cause this is the 1U1 is seeing current draw when the machine is un occupied .I have had this...
Seen that one too, I found that the fan reqest relay sticking. Not sure on the designator though. Also check to see if there is current draw when coming occupied. Rick
hey I know you !
usally shipped in the drain pan area! Rick
You got it. Yes it will!
Is the study guide you have like a pre test? I am taking it in about a month. Rick
What type of air handler do you have? What is the model? Is it a 2 circuit type? I will need more info to help you out. Is your TXV rated for 50 tons?
At my office we are more than happy to help our customers with any literature that they need. Just post a message and I will try to get you any info.
not bad , but you should have ran the overflow pan drain lines seperately!