Type: Posts; User: sherycool
thank you mchild for your reply ...
when i put a/c on cooling mode this code E6 appear on control panel what is this code mein.... thank you...
what is code E6 mein in "general ac split unit 3 hp."
what is code E6 mein in general ac split unit
I agree with ( oloenneker)
(It's a revenge war, and a war for Oil... nothing more, nothing less. It's all about control of the Middle east and we all know it... )
after 37 years in filed I learn more every day from such sites and forums.
here are those 10 reasons in brief as related to 3ph motors
2-single phasing by loss of one phase of 3ph.
3-high or low voltage.
if the winding resistance is ok I think it hard-line comp.
try the four way to run that comp.:
1- hige start tourq .and ruber hamer on comp. (start cap. 80-150 uf)
2- chang the dircion of rotiton...
3 defrost 40 min.per day is OK but keep door closed as possible and for short time.
yes top side up
(but of course, I am already knew that ... )
thank for your replay...
I say D is the correct answer > we understand what hapend in evap.ref.the heat is absorbed is latent heat which change the state of ref. from liquid to vapor these changes of state occur at the same...
voltage is correct
components is correct I change relay.
their is no a run cap in the circuit. current relay and start cap. only.
I will Check the resistance of the start and run winding
I have a problem whit supermarket deep freezer>
deepfreezer factory charg.
comp. danffos 1/2 hp.
comp. run for frist time ok.
when restart srart cap. explosion.
I chang relay but no chang.
YOU FORGET TO DO ONE THINK IT WANTE TO FIXED RETURN AIR TUBE ..WHEAR THE PROBLEM THIN....GO OOOOOOOOOOON.
LEAK IN CON. NOT TAKE 2 YEARS ..LEAK IN EVAP. IS OK>>
I FACE SAME PROBLEM ONES DAY ..
GOOD JOB MY FREIND..
I HAVE A CHART RECORDER FOR temperature IN MY CENTER TOO..
GOOD JOB IAM SURE YOU ON TRAC..
ASTEAY BAGK MY FREIND .......IT NEED BILT CAVER.
RIGHT JOB GO OOOOOOON...
GOOD JOB MY FRIEND.