Type: Posts; User: marklouisville
Search took 0.00 seconds.
Just to your point.....its snowing today and 32F outside.
I raised the set point to 68F and set it on hold - inside temperatures range from 67-70
At this temperature the house...
I think that we are getting closer:
The basement is not currently finished or heated - but am including this in load calc.
We have been at a set point of 66 with an aggressive setback of 62 during...
Sorry, we have not done another blower door test yet.
I went back and checked HVAC-CALC and caught a few errors
I'm right at 70K BTU - its a walkout basement so there is about 20K heat...
800 to 900 annual therms, Monthly ranges from 13 to 150.
We run the home cool - stat is usually set to 66, Probably will run 68 with the more efficient furnace.
Blower door test was run before the...
Would appreciate help with a choice between an 80,000 or 100,000 Btu Bryant Evolution 987M furnace (97%AFUE)
Original furnace is a 140,000 BTU 80%.
Location is Louisville, Colorado (suburb of...