Type: Posts; User: rlchvac
Search: Search took 0.01 seconds.
OOPS sorry - didn't catch the KAV. I went thru a load of problems with the Bryant heater's with standing pilots.
Had the same plate as a fix at first.
After the baffle, they still had problems & came out with a larger orfice for the pilot. If you still have pilot problem they say to install a pilot relite kit.
Yes it checked out Ok - I'm going back in fall to do a full furnace check.
It was installed by a registered plumber.
Corrected install with new 2 ton condenser.
Hehe - good one coolwhip
That is a 6" flex for the return & 8" for the feed.
2.5 ton A/C & 100,000 heater. For a house that only needs 2 Ton & 50,000
Had a call on a 2year old system , customer said the air filter never gets dirty. Could not believe what I found !!
Should'nt you have a low water cutoff installed ?
Just got called into an apartment complex here.
Units are split heat pumps - EMI thru the wall
units with TexFan airhandlers and electric heat
in a small utiliy room
1- Has anyone had a...
Needed to turn to clear intake pipe.
5 90's on exhaust- 4 90's & 1 45 on intake
2" goes vertical to 2.5 horzontal run about 18' long
Systems working like a charm. Homeowner loves the comfort.
They claim they never felt so warm.
19x7 (1/2" insulation) with variable speed motor in furnaces
They are only 80,000 & 100,000 btu heating only furnaces.
All the existing ducts are insulated. Wanted to keep as much as possible(Cool damp basement). Used the return boxes to gain some height &...
Sorry old rusty pulse heaters were take out before I could get the before pics. The is a three story stone house. Originally coal heat before the Pulse furnaces went in.
One 80,000 furnace heats the...
Removed old rusty Lennox Pulse Furnaces & installed 2
Bryant 90% Variable 2-stage Furnaces.
Sorry forgot to take before pics
They are new - Just painted everything white per homeowner's request
They sure are - 1" & 4"x4"
Ground had been like this for years.
Pipes driven in at least 4'
I like the Fancy Chimey Caps too
12" between units & 12" off wall
2 - 2ton units
Yes is it pressure treated wood &
The reality sometimes dictates things
that can't be helped
[Edited by rlchvac on 09-15-2003...
I don't remember who gave the idea of pipes with 4x4's for heatpumps but i used the idea for this install
They are in the back of the first floor apt.
It is a laundry/utility room for both apts.
This was a contractor with an average of 3-5 trucks running all year- LARGE yellow page at too
[Edited by rlchvac on 12-01-2002 at 01:53 PM]
One of our larger advertizing hack's in the area installed new furnace & a/c. Never told tennants that it wasn't finished. That was in 1997 & YES THEY WERE FUNCTIONAL !!!
I came across this as an...
Went on a call to replace thermostat in 1999.
This is what I found. (Look at date on equipment)
1st furnace is a counter flow & the 2nd is an upflow -
in a duplex.
Results 1 to 25 of 41