Type: Posts; User: oldhweller
I have a spare XL15b, if you need it. Thanks. Mike
Seems like Kefah has disappeared from the thread, leaving us to argue among ourselves.
Use your database backups and install on another computer
Do either of these devices have active biasing resistors? That is, pull-up and pull-down resistors to the the rail voltages? Add a small 12v DC power supply with 10k ohm resistors to the + and -...
Because we have a service contract with HW for just this thing, HW installs the service packs. We both work together to make sure no problems arise. We have XL50s,Xl500s,XL800s,XL10(of various...
We have access to our HW techs and they have TAC(Techanical Assistant Center support). Very seldom do we have to go past them. I used to work in TAC on this product, and the HW techs have known me...
We are an EBi customer and support ourselves. Yes there are questions we have, but our service contract covers this. No equipment covered. Where are you located? Thanks. Mike
Huge amounts of documents available. We just need to know what controller. If it is XL500-5000 series, do you have CARE? If not you're SOOL!!!:gah:
Are you using the Modbus interface or is the system standalone? There are 2 options for cascade. Each has a different sequence. Check the literature. I have several of these setups and they work...
You obviously don't have any idea what you're talking about. If you've never done any EBi systems, you should not say anything.
Having worked for them I agree.
I have a Fujitsu ductless mini-split with the wired controller. It comes shipped with the configuration to use the indoor unit sensor not the t-stat sensor. See EN-5 page of the compact cassette...
Has any one experienced condensor fan motor failures on these 30rba units? We have a 250 and a 125 and have lost about 12 motors. Failure mode is always bearing failure which then causes rotor to...
Are these equations really accurate in the real world?:putergreet:
I have always floated ALL inputs. NEVER take to chassis or electrical ground.
:putergreet:Does anyone have a LNS plug-in for the Veris 8920-3 Modbus to Lon integrator. I know Veris doesn't support it any more and I can't get it from their website. TIA Mike
Either will work well. Floating control takes 2 DO's where modulating takes 1 AO. Float control motors only use energy when moving. Modulating uses energy all the time. Your choice, but remember...
I don't believe that these are communicating t'stats.
2 gigabit = 256m bytes(128M+128M)::putergreet:
As said before, use the help files. I put in my first EBi in 2000 without any schooling, but with 30 years experience of HW systems. EBi, as said, is so powerful that its mind-boggling. However,...
And then the fight started.:censored:
And then the fight started:angel:
Tridium is Honeywell.:cheers:
I have an extra one I would be willing to part whith, if you need it. Thanks. Mike