Type: Posts; User: Snides
The HOST sortware came on 11 x 3.5 disks
As mentioned below, the GCMA-114 is the HOST lan card. There are a number of PC issues along with the QNX operating system.
You have some decisions to make.
Early GCM's (84 series) no long...
The GCM will have a "block" of programming for the MZ1. Only minor adjustments are available. They are preconfigured.
The GCS is only an I/O panel.
You will find "block" for the I/O in...
TAC now have a XP version of XPSI.
You will need a contact within TAC to get a (legitimate) copy.
Are you telling me you really can get 20-25% "margin" on new work?
We are happy to break-even on new work.
The work itself is obviously no harder in OZ, but we have to deal with inept...
Not sure how familiar you are with BC NW8000 but, the GCM 84 has come to the end of its supported life. SIGNAL is a GUI not a programming tool. XPSI in relation to a GCM is not a...
[QUOTE=Texasgrand;2916542] Low up front cost.
Just spec what you want and put it out to open tender.
Then start a dutch auction.
If your specs any good you should be able to force the lowest...
We have been using the Belimo option but the valves mentioned appear to be a hole in their range.
I am looking for up to date actuator options for the above valve body.
24vac supply 0-10vdc or 4-20ma control.
Many of the now TAC options are no longer supported. MP-381 seems and...
Good news Destronger, in this business you get to learn every day.
Why does the JACE have 64 I/O capacity? What are people using that for?
From our perspective.
Chiller plant control. HLI to chillers, VSD's on pumps, Modbus to water treatment, elect and water...
Its a place but not my work.
The honeywell component of Tridium's sales are only small in comparison to the rest of Trdium's SI's and OEM's.
If we expand your logic a little further, If UTC were to buy out Automated...
Check your messages again.
Check your messages. User name and Password detailed.
You may have not meant it the way I read it but "I think I'm past the learning curve" is probably one of the most arrogant comments I have read on this forum to date.
After over 35...
We have been Tridium Si's for quite a number of years now.
From a customers stand point Tridium has to be a very good fit for campus type installations.
However, as jogas has said,...
I'm looking for a DP sensor that can "accurately" measure air pressure down to 5pa. Looking for a range of say 0-10pa
Does any know of a supplier for the above?
TAC are now the vendor.
There is a Win 97 version.
The ASD driver allows you do do all of the GCM functions.
All of the MN-FLO attributes are available.
We have done this a number of times.
GCM-ECH-001 is GCM to GCM LAN.
Appears you have multiple GCM's
If this is the case you would have to stay with the GCM driver.
However, if you look at the cost of replacing a...
GCM-ECH-001 is just a comms module. It is not Lon compatible.
1. Retain GCM and use GCM driver within JACE controller. R.2 & AX versions available.
2. Remove GCM and...
Using the "arrow" keys, scroll left or right until you get to "Block", press enter.
Again scroll left or right to "edit" and "enter".
Now scroll down until you get to "Week" blocks. Look...
Not sure what h/ware you have but this may help.
To-date we have only had TAC/Invensys AX available to us with the Lon driver.
Now how best do I put this.
I guess logic tells me that "long term" it maybe not be in...