Type: Posts; User: xxcels
I just brought a uniweld vacuum..Works great!
Find the leak first with some leak detector (soap bubbles) before you charge it or else you some throwing money away.
If you changed the capacitor then the motor might be bad
I need to find a good company to work for too
I was thinking of just Fabing one of my own but i'll go double check everything first like you said..Thanks
I have a condensate pan that rust through. But can't seem to find the pan anywhere. There is no unit # anywhere except for the compressor.
GL! i'm looking to take the NATE test too
MIGHT BE THE BOARD
Just a grey company tee
They said it's U.S made. Cost about $400-$600
Anyone ever own a Uniweld Vacuum pump? Any feedback would be appreciated..
lol...damn you drunk
I got 24v at the board. I traced it to the unit. The wires go into this little gray box (not sure what it is call) that clamp around a blue wire going into the fan relay. I am pretty sure that is...
After some troublingshooting today I notice on the ccn that the SFS (supply fan status) is off. But the blower fan is running. I reset the unit. It goes through its normal heating operation but the...
yes, the preimer link is mounted on the duct below the unit.
That's what I thought too that the OAT is only for the Econmizer but it seem to be locking out the unit. And there is no code for...
Working on a Carrier M# 48HJ3006. The unit is on CCN. It is telling me there is a OAT sensor failure (reading -40). Is it effecting the heating cycle? I have to reset the unit to start up the...
mmm ok ill give it a try, but that does not explain the owner telling me the furnace wont kick back on after a couple of cycle. He have to reset the whole furnace.
yes it does have a three wire.. is there any way for me to test it?
Owner call me to take a look at his furnace. He said he have been turning the power switch off and on to reset the system when the furnace wont recycle. I...
After we did a new install 80%..customer call back the next day saying there is no heat. I went out to check it out. He pointed me to the return grill and said "its cold here"
There seem to but no Data plate on the unit but the cover of the manual
M# 174-0 Series
Yes, I checked the pilot and there is a strong pilot flame. I putted a new thermocouple...
So I have to get a slow opening valve? I'll look into it.
Yes, I am reading 3.5 at manifold. I haven't check the inlet yet. So you are saying I might not have enough gas pressure?
Need help working on a Residential climatrol furnace. I forgot the model #. I just installed a universal 24v gas valve and new thermocouple the other day. I got a call back today. Tenant complaint of...
School first.... it help me get a job.