Type: Posts; User: aircooled53
Oh, ur a real funny guy. :beat:
Any HVAC guys out there, got friend in need of 1/4hp -230v outdoor motor,PLS if you can help me out sell me a motor, so I can put it on for his a/c to work .Have some mercy for old man. Email...
Carrier - is BDP
So, which dealer provided you the best information on design, load and the adapt of new system to your duct system. I would recommend Variable DRV system...
Does Not effect airflow, why remove and chance making a leak on coil. leave it there; can't hurt anything.
It happens allot here in Fort Worth area also, on church we set condenser on got hit twice in 3 months 25,000.00+
:angel:Smart = Honeywell
It was called VACUUM back in my day, if you have P/T not measure accurate ,recover refrigerant, vacuum, check with micrometer and re-charge, NO more non-condensables
I'd stay with heat pump and change to more efficient drive air handler. Variable drv air handlers remove humidity very fast and with right size outdoor heat pump, you could see allot of...
I will ship it Fed-Ex and all payments are cash this meter is new.
Paid 349.00 when purchased I'm no longer in industry.
Digital HVAC Analyzer
Measures Temperature (ºF) and Humidity (%RH)
Measures Dew Point (ºF)
Measures Velocity (FPS) and Volume (CFM)
Measures Power in BTU/HR
Direct Readings -- no additional...
I have a good meter for sale for $150.00 cash/money order
What cause did you find the need to replace sensor? AIR ?
Frankenstein --It's A L I V E..
Anytime system is open, vacuum and drier and recharge is necessary. If R410 A this is critical to performance of system.I would call contractor back and ask for vacuum/drier and recharge with R-410a.
A buddy has been working on Scottsman ice machine 1979 model, works great in winter fills up and runs allot of ice.Summer comes and it won't dump ice, system is R-502 charge was weighed in. New tray...
The use of existing coil is fine;as long as the system is flushed w/cleaner..
Install/txv and LL drier, and your set.
It is what is covered by Home warranty and the rest is necessary to complete a proper installation of replacement coil.:gah:
Not trying to be mean, but we can't see the unit, or where you are. I would try turning off thermostat and letting it reset.Set cooling temp, then turn on see if unit starts.If not then call local...
Let the Infinity do it's job. Just use it for awhile until you get used to the new feel of having a v/drv unit...:whistle:
I agree same here in Texas, hot= falling btu's of cooling after 95* in 410A..
Yes, I did it in 1976 and never looked back, after Army and climbing radio towers wasn't what I wanted to do.:.02:
Take the York and replace it after 2 years..
Check condenser Coil/airflow
I heard that you can buy units now with no refrigerant in them to get around the new R-22 laws..
Was informed that new systems are charged w/ nitrogen and just pull vacuum and add R-22..
George \Without/ Bush didn't catch Bin Laden , he was too busy with Saudi Arabia buddies..:gah: